AC air handler squealing or grinding noises. Though most air handlers have direct-drive motors, some older units may be belt-driven. Squealing sounds from a belt-drive air handler generally occur when the belt that connects the motor to the blower slips. In most cases, the belt is improperly aligned or worn and needs replacement. Follow the instructions above under Air Conditioner Not Blowing Air and refer to your owner’s manual.
Don Vandervort has developed his expertise for more than 30 years, as Building Editor for Sunset Books, Senior Editor at Home Magazine, author of more than 30 home improvement books, and writer of countless magazine articles. He appeared for 3 seasons on HGTV’s “The Fix,” and served as MSN’s home expert for several years. Don founded HomeTips in 1996.
Our unit is 16 years old and we've had it checked out recently since it seems to be running excessively. Over all the tech says it is putting out well; it's the correct size, we have no shade and we've been having extreme heat with high humidity. The info you provided is very helpful and will help us make an informed decision when the time comes. Thank you so much.
Indoor Coil -- The indoor coil is a heat transfer device. It absorbs the heat from the inside of the house and passes it on to the refrigerant and is pumped outside. Dust that builds up on the coil can hamper its ability to absorb heat. High heat transference coils use very thin metal. Airborne chemicals can cause corrosion which leads to leaks. The constant vibration of the compressor can also cause solder joints to weaken and leak. An indoor coil may operate for weeks with a tiny leak, and you may not notice the loss in performance right away. As soon as a leak is made known, it should be replaced or repaired immediately.
Do you live in a historic home and want to tie your new system in to work with existing features? The price will go up to do the job right. All of these things add up to slow down the HVAC company, which takes more time, which costs more money for labor and parts. This is especially true if they are a legitimate company which is licensed, bonded and insured. Simply put, this is the “X-Factor” in your HVAC installation cost. Again, you could get people to do it for cheaper…but you won’t be happy with the results, I promise.
Before opening the electrical cover on the A/C unit, be sure to shut off all power to the compressor unit and the indoor furnace or air handler, and verify that it is off. Note that this may mean shutting off a circuit breaker that serves the furnace and air handler, and then, near the compressor, pulling out the disconnect block (or shutting off the 220-volt power) to the outdoor compressor.