Capacitors -- Capacitors help your HVAC motor start from a standstill. Over time they can weaken. As they weaken, they cause the motor to run hotter. This can shorten the life expectancy of your motor. Once a capacitor fails, the whole motor will stop working. You usually won't notice that a capacitor has weakened until your motor stops turning on.
In addition to the information below, see these two articles for the general care and maintenance of your air conditioner: Preparing Your Air Conditioner for Summer and How to Replace Furnace & AC Filters. Most noteworthy, you should replace the filters at least twice a year, before the heating and cooling seasons. For information on furnace problems, please see Furnace Not Working.
7 To test it, turn the thermostat to OFF, reset the power at the disconnect next to the compressor and the main panel. Set the thermostat to a temperature below the room temperature, and then switch it ON. To avoid straining an air conditioner’s compressor, wait at least five minutes between turning it off at the thermostat and turning it back on. You should hear the outdoor compressor run and see the fan turning inside the top. If the fan isn’t turning, look for an overload button or switch to reset (not all types have this).
Natural ventilation is the ventilation of a building with outside air without using fans or other mechanical systems. It can be via operable windows, louvers, or trickle vents when spaces are small and the architecture permits. In more complex schemes, warm air is allowed to rise and flow out high building openings to the outside (stack effect), causing cool outside air to be drawn into low building openings. Natural ventilation schemes can use very little energy, but care must be taken to ensure comfort. In warm or humid climates, maintaining thermal comfort solely via natural ventilation might not be possible. Air conditioning systems are used, either as backups or supplements. Air-side economizers also use outside air to condition spaces, but do so using fans, ducts, dampers, and control systems to introduce and distribute cool outdoor air when appropriate.
If your compressor doesn’t have an overload button and you hear it humming or buzzing, poke a screwdriver or stick down through the top grille and try to spin the fan blades clockwise. If doing this gives the fan enough of a boost to get it going, the unit has a faulty capacitor that must be replaced. See How to Test and Replace an AC Run Capacitor, above.