Alberto said they were busy but could either install on the upcoming Saturday. We were going to be out of town and said unfortunately that day did not work. He then proposed the upcoming Tuesday as a possible solution, but just had to confirm with another appointment. I said great. I will review the estimate and call your office to confirm I want to move forward with the install.
In modern buildings, the design, installation, and control systems of these functions are integrated into one or more HVAC systems. For very small buildings, contractors normally estimate the capacity and type of system needed and then design the system, selecting the appropriate refrigerant and various components needed. For larger buildings, building service designers, mechanical engineers, or building services engineers analyze, design, and specify the HVAC systems. Specialty mechanical contractors then fabricate and commission the systems. Building permits and code-compliance inspections of the installations are normally required for all sizes of building.
Typically speaking, the lower SEER, more basic models are also more reliable. Reliability is big with us, so we steer clear of features with reliability issues, and it’s as simple as that. When you factor in the price of repairs and the extra expense of the 21-SEER, you may actually lose money! 16 SEER is the sweet-spot, and it is key to reducing your HVAC installation cost.
Installation: Replacement is quite easy, especially when an old refrigerant line set can be used. If the set is worn, it’s much better to pay the extra $400-$600 to replace it rather than risking it leaking later. When your AC loses refrigerant, you lose your cool air and the compressor is at risk of failing. A new installation means installing a coil in your furnace or air handler, running the line set between it and the coil in the condensing unit and adding refrigerant, if needed. Most ACs come pre-charged for 20-30 feet of line. If the line set is longer, a small amount of refrigerant is added.
Energy efficiency can be improved even more in central heating systems by introducing zoned heating. This allows a more granular application of heat, similar to non-central heating systems. Zones are controlled by multiple thermostats. In water heating systems the thermostats control zone valves, and in forced air systems they control zone dampers inside the vents which selectively block the flow of air. In this case, the control system is very critical to maintaining a proper temperature.