Tip – Be careful with change-outs. Ductwork deteriorates and sometimes has to be replaced. It is only if the ductwork is in fantastic condition that you should get a change-out without ductwork (Remember – the ductwork has already been there for 15-20 years, and now it will be there another 15-20…it has to be in good shape). However, many HVAC installation companies like to push change-outs because the ductwork is the most time consuming part of the job, and a change-out is quick, easy money. Realize that it’s only about 15-20% of the jobs that qualify for a change-out, so be careful.
Clean the condenser fan blades before the start of the cooling season. Brush any dust or debris off gently and then uncover the condenser coils, gently cleaning the dirty side. Then wrap the motor and other electrical components in plastic bags and gently spray from the inside with a hose. Now check the base pan under the unit and clear it out of any debris that has gathered.
The liquid refrigerant is returned to another heat exchanger where it is allowed to evaporate, hence the heat exchanger is often called an evaporating coil or evaporator. As the liquid refrigerant evaporates it absorbs energy (heat) from the inside air, returns to the compressor, and repeats the cycle. In the process, heat is absorbed from indoors and transferred outdoors, resulting in cooling of the building.
If you hear clicking that is followed by a hum or buzz, you’re probably hearing the fan motor attempting to start without the boost it needs from the capacitor. You can almost always conclude that the capacitor has failed. Sometimes you can get the compressor fan spinning (clockwise) by pushing it with a thin stick or long screwdriver poked through the grille. But the chances are good that this might work for one cycle, but the capacitor will fail next time the AC goes on. It’s best to replace the capacitor.