An AC contactor is a $25 mechanical relay that uses low-voltage power from the thermostat to switch 220-volt high-amperage current to the compressor and condenser fan. AC contactors can wear out and are at the top of the list of common air conditioning service failures. Even if your AC contactor is working, it pays to replace it every five years or so. Unscrew the old AC contactor before removing the wires. Then move the wires to the new unit (Photo 6).
If the AC doesn’t turn off, it may be time to clean the condensing unit. Dirty condenser coils won’t give off heat efficiently and will keep the unit running. Another possibility: The contacts on the outdoor run relay may have welded together—something that can happen over time because of frequent electrical arcing at the relay. Before checking the run relay, turn off the power to the furnace and the condensing unit. Next, disassemble the relay and pry apart the contacts. This should do the trick until you buy a replacement—which you should do soon.
Energy efficiency can be improved even more in central heating systems by introducing zoned heating. This allows a more granular application of heat, similar to non-central heating systems. Zones are controlled by multiple thermostats. In water heating systems the thermostats control zone valves, and in forced air systems they control zone dampers inside the vents which selectively block the flow of air. In this case, the control system is very critical to maintaining a proper temperature.
An alternative to packaged systems is the use of separate indoor and outdoor coils in split systems. Split systems are preferred and widely used worldwide except in North America. In North America, split systems are most often seen in residential applications, but they are gaining popularity in small commercial buildings. The split systems are a great choice for small buildings where ductwork is not feasible or where the space conditioning efficiency is of prime concern . The benefits of ductless air conditioning systems include easy installation, no ductwork, greater zonal control, flexibility of control and quiet operation . In space conditioning, the duct losses can account for 30% of energy consumption . The use of minisplit can result in energy savings in space conditioning as there are no losses associated with ducting.
We divided new HVAC installation cost into three groups: first, the Change-Out, which is an installation of just your HVAC components without the ductwork; Full Installation, which is the installation of all HVAC equipment including ductwork; and finally, Full Installation with Features, which is a full installation with additional features such as a zoning system or media filter with a complimentary Ferrari Portofino.
Duct system installation and repairs affect HVAC installation cost. If you’re installing a new forced air heating or cooling system, your home must have ductwork – if you don’t have ducts installed, a new duct system will need to be designed and installed. Your existing duct system may require air sealing to eliminate air loss, helping your new heating and cooling system operate efficiently.
The Chartered Institution of Building Services Engineers is a body that covers the essential Service (systems architecture) that allow buildings to operate. It includes the electrotechnical, heating, ventilating, air conditioning, refrigeration and plumbing industries. To train as a building services engineer, the academic requirements are GCSEs (A-C) / Standard Grades (1-3) in Maths and Science, which are important in measurements, planning and theory. Employers will often want a degree in a branch of engineering, such as building environment engineering, electrical engineering or mechanical engineering. To become a full member of CIBSE, and so also to be registered by the Engineering Council UK as a chartered engineer, engineers must also attain an Honours Degree and a master's degree in a relevant engineering subject.
Consequently, this water must exit the air handler—typically through plastic pipe or a drain tube. That drain tube goes directly outside, often terminating near the compressor, or to a floor drain or to a small electric “condensate pump” located by the air handler. Where a condensate pump is used, it connects to a 1/2-inch vinyl or rubber tube that exits outdoors or to a drain.
Be careful of dishonest HVAC contractors. There’s no magical formula to see if an HVAC contractor is scamming you, unfortunately, but remember that they typically do this in one of two ways: first, they are charging grossly low prices (far below everyone else), or second, they aren’t including what everyone else is. In the first situation, they will charge you change fees, other hidden fees, or they stole the equipment and are passing themselves off as legitimate contractors (very common in California these days). In the second situation, they are charging you a very fair price, but aren’t including what the other contractors are (i.e. charging $10,500 for the installation which is fair, but not including the ductwork which is a scam unless there is some other, complex stuff going on there).
The belt should slip right into place. If it seems to be too tight or difficult to set in place, it may be necessary to adjust the motor mount to provide more slack. Then you can re-tighten the tension once the belt is in place. Check the manufacturer’s specifications for proper tension—in most cases, the belt should deflect about an inch when you press down on it.