Before opening the electrical cover on the A/C unit, be sure to shut off all power to the compressor unit and the indoor furnace or air handler, and verify that it is off. Note that this may mean shutting off a circuit breaker that serves the furnace and air handler, and then, near the compressor, pulling out the disconnect block (or shutting off the 220-volt power) to the outdoor compressor.
But Tim, doesn’t this mean that a less-than-honest air conditioning company can just charge what he wants and say that it’s a difficult job? No. You see, dishonest contractors, typically, aren’t the brightest people (I figure if you’re still reading this, you’re warming up to me so I’m taking off the training-wheels). They aren’t smart enough to take difficulty into account, and will probably get confused if you ask them about it. They will tell you things like, “that’s how much the unit costs,” or “California has a new law that magically adds $5,000 to the price.” Trust me, follow your gut, and you’ll be able to tell who the honest contractors are...or just use one of our ASM-approved contractors.
PickHVAC Tips: First, see the PickHVAC tip above about sizing a central air conditioner. It applies to heat pumps just as much. Secondly, Even if the line set for the new heat pump is the correct size, we recommend replacing the set or at least the fittings. Old lines and fittings are a major source of leaks. When refrigerant leaks out, the heat pump efficiency suffers. Eventually, the unit stops providing heating and air conditioning, and it might break down.
If you hear clicking that is followed by a hum or buzz, you’re probably hearing the fan motor attempting to start without the boost it needs from the capacitor. You can almost always conclude that the capacitor has failed. Sometimes you can get the compressor fan spinning (clockwise) by pushing it with a thin stick or long screwdriver poked through the grille. But the chances are good that this might work for one cycle, but the capacitor will fail next time the AC goes on. It’s best to replace the capacitor.