The University of Virginia - 2005 / The Wharton School of Finance - 2016 / U.S. Naval Aviator 2005-2015. At All Systems Mechanical air conditioning and heating, we believe that the experience our clients have is every bit as important as the products they receive. Simply put, our results speak for themselves, and we'd be happy to help. If you're in the market for a new AC or furnace, make sure that you get a fair price! Try our online calculator; click the tab on the top of this page for more information.
Hi John, Thanks for reaching out, we would be happy to help you connect with a pro for your project. You can submit a request to our pros here: www.homeadvisor.com, browse a list of pros that serve your area here: http://www.homeadvisor.com/c.html, or send your info to firstname.lastname@example.org and a project advisor will reach out to assist you. –HASupport
They were quick to come out and diagnose the problem with my furnace, but I thought the estimate of $549 a bit high to replace the circuit board. So called around and found Leo's Appliance in Concord that sells appliance parts and the circuit board was only $90.49 - that is the retail cost to me, so I imagine the wholesale cost is a lot less. So BEWARE of this company since they wanted $500!!! to replace the circuit board which is located right in the front of the furnace - extremely easy to access. I hate it that you cannot trust repair companies.
If the AC doesn’t turn off, it may be time to clean the condensing unit. Dirty condenser coils won’t give off heat efficiently and will keep the unit running. Another possibility: The contacts on the outdoor run relay may have welded together—something that can happen over time because of frequent electrical arcing at the relay. Before checking the run relay, turn off the power to the furnace and the condensing unit. Next, disassemble the relay and pry apart the contacts. This should do the trick until you buy a replacement—which you should do soon.
Some of these components can be repaired or replaced by the homeowner, such as filters, fuses, and clogged up drain lines. Coils, compressors and the other components are best left to a professional. In some cases, you may have a system that is so old that parts are no longer available or else they aren't up to code. In this case you will have to consider replacing the entire system.
Clean the condenser fan blades before the start of the cooling season. Brush any dust or debris off gently and then uncover the condenser coils, gently cleaning the dirty side. Then wrap the motor and other electrical components in plastic bags and gently spray from the inside with a hose. Now check the base pan under the unit and clear it out of any debris that has gathered.
Tip – Be careful with change-outs. Ductwork deteriorates and sometimes has to be replaced. It is only if the ductwork is in fantastic condition that you should get a change-out without ductwork (Remember – the ductwork has already been there for 15-20 years, and now it will be there another 15-20…it has to be in good shape). However, many HVAC installation companies like to push change-outs because the ductwork is the most time consuming part of the job, and a change-out is quick, easy money. Realize that it’s only about 15-20% of the jobs that qualify for a change-out, so be careful.
They are also often harder to install. A proper location on the roof must be selected that can support the weight of the unit. Then a platform must be built and a drain pipe for the unit must be run along the roof to avoid problems with mold and corrosion. A crane must be used to lift the unit onto the roof while a team guides it into place and hooks it up.
If your central air conditioner will not cool but you can hear it running, it may just need to be cleaned. Whether or not this is the cause of the problem, it’s a good early remedy to try. Plan to do this on a relatively warm day. Never use a power washer for this—it can damage the fins. The following are guidelines; always refer to your owner’s manual. Note: Always turn off the power before cleaning the unit.