Reinstall the access panel and disconnect block. Turn on the circuit breaker and furnace switch. Then set the thermostat to a lower temperature and wait for the AC to start (see “Be Patient at Startup,” below). The compressor should run and the condenser fan should spin. If the compressor starts but the fan doesn't, the fan motor is most likely shot. Shut off the power and remove the screws around the condenser cover. Lift the cover and remove the fan blade and motor (Photo 7). Reinstall the blade and secure the cover. Then repower the unit and see if the fan starts. If it doesn't, you've given it your best shot—it's time to call a pro.
Central home air conditioner service systems consist of two major components: a condensing unit that sits outside your house, and the evaporator coil (often referred to as an A-coil) that sits in the plenum of your furnace or air handler. The refrigerant in the A-coil picks up the heat from your home and moves it to the outdoor condensing unit. The condensing unit fan blows outside air through the condensing coil to remove the heat. The condensing unit houses the three parts replaceable by a DIYer: the AC contactor, the start/run capacitor(s) and the condenser fan motor. The condensing unit also houses the compressor, but only a pro can replace that. The A-coil has no parts that can be serviced by a DIYer.
Many homes have a forced-air HVAC system. Both the heating and the central air conditioning units share a ductwork system where they either push in or pull out warm or cooled air. There are also heating and cooling systems that don’t require ductwork — such as ductless mini-splits — but work on the same principles of heat exchange. The national average to hire an HVAC specialist is $2,920-$3,670, with costs varying depending on the work you need done and the equipment you are installing.
Compressor -- Compressors are outdoor components in your system. The compressor is the pump that circulates the refrigerants through the air-conditioner. You can hear it when it's running so you'll know if it's working just by listening. If it starts getting louder, your compressor is about to fail. If it makes no sound when it should be on, it has already failed. Compressors fail for a number of reasons. Most often they fail due to strain from another failed part such as the fan motor. Electrical storms can also damage compressors. If the sound from the compressor gets louder or if you see a decrease in performance, you should have your compressor checked. A failed compressor will not heat or cool your house.
Don Vandervort has developed his expertise for more than 30 years, as Building Editor for Sunset Books, Senior Editor at Home Magazine, author of more than 30 home improvement books, and writer of countless magazine articles. He appeared for 3 seasons on HGTV’s “The Fix,” and served as MSN’s home expert for several years. Don founded HomeTips in 1996.
To qualify for a tax credit from the federal government, you must save the manufacturer's certificate from your system. The IRS won't require the certificate at the time you file your federal tax forms, but they recommend keeping it with your records in case of an audit. It proves that you purchased a qualifying product. The government offers tax credits for:
Service Experts Heating and Air Conditioning was founded on the basis of providing customers with the best heating and cooling practices in the industry. Since its inception, Service Experts has been dedicated to community, providing the top of the line HVAC products and services in your area. If you want more information about your local HVAC leaders, call us at 866-397-3787 or set up an appointment with us online.
SEER is useful for comparing one model to another much in the same way that a car's calculate MPG is useful. It's not an accurate prediction of exactly how efficient the system is, but it can tell you which one is more efficient. Also, since SEER is based on a "cooling season", what region you live in will determine how long or short your cooling season is.
Before opening the electrical cover on the A/C unit, be sure to shut off all power to the compressor unit and the indoor furnace or air handler, and verify that it is off. Note that this may mean shutting off a circuit breaker that serves the furnace and air handler, and then, near the compressor, pulling out the disconnect block (or shutting off the 220-volt power) to the outdoor compressor.